Illustrate the installation steps and methods of the wall AC
Nowadays, when decorating, there are more and more choices of air conditioners, and the types and brands are dazzling. Especially in recent years, the hidden wall AC installation can be hidden in the ceiling and does not affect the home design. More and more houses choose to install it. Is it that good? Today, Wall AC company in Tregear will make a big comparison on the construction and maintenance of wall-mounted air conditioners and ceiling-mounted air conditioners, so that you can find the most suitable air conditioner.
Wall AC Installation location
- The installation height of the wall-mounted indoor unit should be more than 150cm higher than the ground;
- There should be a space of more than 5cm between the wall-mounted indoor unit and the ceiling above and the walls on the left and right sides;
- The wall-mounted indoor unit should be more than 5cm away from doors and windows to avoid excessive air-conditioning loss.
- The wall-mounted indoor unit should choose a location with good indoor air circulation so that reasonable air convection can be formed indoors.
- Try to install the wall-mounted indoor unit in the middle area of the house, so that the cold and hot air can be sent to all corners of the room.
- There should be no obstacles at the air inlet and air outlet, otherwise it will affect the cooling effect of the inverter air conditioner.
- The installation height of the wall-mounted indoor unit should be higher than the visual distance and more than 0.6m from the ground obstacle.
- Take care to avoid direct sunlight on the body, and no heat source or water vapour nearby.
Installation method of internal machine fixed hanging plate
The connection method is as follows:
- Straighten the connecting piping coiled into a roll to facilitate the extension connection of the pipeline;
- Remove the protective cap of the indoor unit connecting pipe and prepare to connect;
- Quickly connect the thin tube (liquid tube) of the cold pipeline of the wall-mounted indoor mechanism with the thin tube (liquid tube) nozzle of the online piping;
- Connect the mouth of the thick pipe (trachea) of the indoor mechanism 1 cold pipeline with the mouth of the thick pipe (trachea) of the online piping.
- Tighten the Nazi on the online piping to the thread of the pipe of the wall-mounted indoor unit.Refrigeration pipeline moisture-proof and waterproof treatment
- After the pipeline connection is completed, make sure that the connection is tight, and then wrap a layer of insulation cotton on the connection interface of the refrigeration pipeline.
- Use waterproof tape to fasten the two ends of the insulation cotton.
Lengthening of the drainage pipe
- Use a drainpipe to connect with the drainpipe of the wall-mounted air conditioner indoor unit to increase the length of the drainpipe;
- After the drainpipe is connected, wrap the joints tightly with waterproof tape to prevent water leakage.
The final installation process of wall AC
- Pass the wrapped refrigeration pipes, electrical cables and drain pipes through the wall holes and extend them outside the house.
- After the pipeline extends out of the object, the wall-mounted air conditioner can be hung on the previously installed fixed hanging plate.
- Hang the wall-mounted air conditioner on the buckle of the fixed plate and move it back and forth to see if it is secure;
- Grasp the front part of the wall-mounted air conditioner with both hands, and press the wall-mounted machine against the hanging plate until you hear a “click” sound;
- Installation is complete
Nowadays it has become easier to get the wall mounted air conditioner installed since in Tregear city, we obtain the services of getting the air conditioner put quickly, in which only a call, an expert air conditioner installer comes to your house or workplace.
If you also want to get wall mounted air conditioner installed in your house or workplace, then you can contact on the phone numbers mentioned below.